Does your Galena, MO home or business need expert HVAC service? Count on All Seasons Comfort Systems to provide the heating, air conditioning, ductwork and indoor air quality services you need!
Our technicians are highly trained and treat you like family. Read our reviews to find out why your Galena, MO neighbors consider us to be their local HVAC company!
for Galena, MO
Our Reviews by City
BJ - Galena, MO
Aubrey, the All Seasons service tech was professional, friendly, and knowledgeable. He efficiently repaired our a/c, had the need parts with him and thoughtfully answered all of our questions even after performing the repairs in the searing 100 degree heat. All Seasons service price was reasonable and we were appreciative of their prompt response.
He is a really good representative of your company and device
Jan - Galena, MO
He is knowledgeable and will trained.
Gary - Galena, MO
They did great work in a timely fashion
Mike - Galena, MO
Prompt service, very courteous
Great service, knowledgeable Tech
Cecil - Galena, MO
Logan Stover was very professional, polite, and diligent.
Bob - Galena, MO
Aubrey resolved my problem with the filter sizing and I am very pleased with the new filter.
Teresa - Galena, MO
Brad - Galena, MO
Fantastic service from Logan
Dawn - Galena, MO
Logan really explained everything he was doing. I need to stay with him because of the cats so it helped to see there was breakers in the furnace. And how he tightened screws due to vibration and how he cleaned coils to keep the system clean. So much in ffg ormation thank you Logan.
Terrific Service, Great Price.
Ruthann - Galena, MO
We were out of town when our 15 year old furnace developed a coil leak. Logan called us & discussed various options with us. We decided to go with a new furnace. All Seasons personnel got us the new furnace, coordinated with our neighbor’s schedule & was able to install the new furnace during the same week (earlier than they quoted). The price was great!! Service excellent. On both visits, Logan called & kept us posted on his progress.
Very nice experience
Mark - Galena, MO
Aubrey was very efficient and knowledgeable. He did a great job.
Ron - Galena, MO
All Seasons responded very fast and Aubrey did a great job determining what was wrong and fixing our air conditioner
James - Galena, MO
He was very thorough and professional
John - Galena, MO
Outstanding service. Logan Petro Is certainly very well-qualified and his customer service is equally outstanding.
Minor - Galena, MO
Knowledgeable and great customer service. Thanks
Scott - Galena, MO
Dan - Galena, MO
On time went over everything
John - Galena, MO
Response from All Seasons Comfort Systems LLC:
John thank you for the 5 star review! So happy we could take care of your heating and cooling needs and look forward to serving you in the future!
Complaint of no heat. Diagnosis- Found loose or blocked contact on low voltage going to contactor. Solution- Got wasp nest out and tested system. Looks good at this time.
Came out for Condenser Fan not coming on. Found that bad run Capacitor was the problem replace Capacitor and got the system operating properly.
Performing a planned maintenance agreement heating checkout on a Lennox communicating heat pump system. Checking filter. Checking wiring. Testing emergency strip heat operation. Checking refrigerant charge on system. Testing outdoor electrical components. And testing defrost functions.
Performing a dual fuel heating tune up on a Goodman gas furnace and heat pump. Found gas leak immediately on gas valve. Shut off gas, re-sealed connection, turned gas back on, and then rechecked for gas leaks. No more found. Then completed system checkout on furnace and heat pump. No other issues found, system running properly at this time.
Troubleshooting a no cooling call. Outdoor unit not running. Found no 24v call at outdoor unit. Verified 24v from transformer. Found broken wire at outdoor unit. Cut back thermostat wire, remade connections, and tested system. System running properly at this time.
A.c not cooling on mobile home system.
Performed a full cooling inspection on Goodman equipment. Checked all wires and safety switches. Found some duck work hanging low to the ground. Tightened up duck work. Checked for air leakage. Found a leak in another part of the ductwork. Repaired all duck work. Performed safety testing to ensure no leaks at this time. Unit is now operating properly at this time.
Faking mini split leaking water found line set not covered and lines condensating pulled insulation tight to cover line
Complaint of goodman/carrier a.c not cooling. Diagnosis- Found low subcooling and high superheat, low delta T. Solution- Added 1lb of R-22. System cooling properly at this time.
Bid on total system replacement on old York a.c and gas furnace.
Complaint of no a.c, indoor unit running outdoor unit off. Diagnosis- Found shorted Dual Run Capicitor. Solution- Replaced Capicitor with new, checked system charge and amp draw of motors. System looks great at this time.
Servicing a Rheem heat pump system with a leaking condensate drain line and performing a system tune up. Cleared condensate drain blockage. Tested drain. Cleaned coils. Checked system charge. Replaced air filter. And checked overall system performance.
Working on a Ruud heat pump that is leaking water. We found that the drain pan was full of rust and plugged the drain.
Came out to do a cooling tune up on a geocomfort geothermal heatpump. Found that one of the four zone dampers were bad. And found that the system was under preforming in cooling mode. Was able to dial the system in by adding water. Got the system operating properly.
Came out to install a low pressure switch on a lennox heatpump. Found that the switch was not working after changing Reversing Valve. Got the switch installed and made sure the system was operating properly.
Came out for reeheem system not cooling found start Capacitor and run Capacitor bad replaced them to get system operating properly
Came out for lennox air handler making noise. Found that there was insulation in the blower causing it to be out of balance. Removed insulation and repaired cabinet to keep it in place.
Installing A blower control board in a Gibson heat pump
Working on a Mitsubishi mini split that is not cooling properly.
Installing a blower and blower wheel on a Lennox gas furnace.
Troubleshooting a no AC call. Found Lennox heat pump running in heat. Found Ecobee thermostat not setup correctly to energize the reversing valve in cooling. Reprogrammed thermostat to energize reversing valve in cooling. Verified cooling operations on system. No other issues found.
Working on a Geo comfort geothermal system that is continuously running.