When you need expert air conditioning, heating, indoor air quality and duct services in the Kimberling City, MO area, you need All Seasons Comfort Systems. We’ve proudly served residential and commercial clients since 1985!
Learn more about the heating and AC repair services we’ve completed in Kimberling City, MO and see what your neighbors are saying about us!
for Kimberling City, MO
Our Reviews by City
Quick service. Very professional and thorough.
Ron - Kimberling City, MO
Yancy was friendly and did an excellent job.
Great Customer Service
Joel - Kimberling City, MO
Yancy was great as always. Very efficient, polite & professional.
Allen - Kimberling City, MO
First class and took the time to explain
Great service - as always!
Chris - Kimberling City, MO
I really appreciated the thorough work that the two service guys did today. They carefully looked at numerous aspects of the system and were able to get the system performing much more effectively. And, they were very polite and courteous.
Linda - Kimberling City, MO
Very helpful and informative on what was going on. Made me confident he knew what he was doing.
Bonnie - Kimberling City, MO
Answered all my questions. Was very clear about system how it works etc
Great job. Lifelong customer now.
Sharon - Kimberling City, MO
Great preseason check
Bill - Kimberling City, MO
Robert - Kimberling City, MO
Logan is knowledgeable and very professional. Good communication and very efficient
Robert - Kimberling City, MO
The service was very thorough and Aubrey explained everything. We appreciated the Covid precautions and wearing the shoe coverings. Thank you.
Pat - Kimberling City, MO
Timely and great service
Gary - Kimberling City, MO
Awesome Service. Very knowledgeable.
John - Kimberling City, MO
Logan was very professional and knowledgeable.
Great service. A lot of help.
Scott - Kimberling City, MO
Good experience. Helped me set up remote internet.
Sandy - Kimberling City, MO
Terrific service! Great communication, attention to detail, made me feel comfortable and informed. All Seasons is my go-to company for heating and cooling needs. Thanks for getting my WiFi thermostat up and running Logan!
Sam - Kimberling City, MO
Joan - Kimberling City, MO
Service was very good. Pricing seemed good. Have nothing to compare it with
Patricia - Kimberling City, MO
Yancey and Michael were very thorough, professional, and efficient! I really appreciated the explanation of the inspection and results, along with needed advice about the split system and the heat pump. Yancey provided much needed education on the most efficient use of the cooling systems especially during high heat humidity. They both left me feeling more confident and better informed! I look forward to future service from your team.
Debbie - Kimberling City, MO
Logan was very proffession and kind!! He went above and beyond to help us out. I just wish we could have been given a quote before the work was completed.
Jim - Kimberling City, MO
All good showed up on time guys were knowledgeable and thorough
David - Kimberling City, MO
On Time and Polite
Todd - Kimberling City, MO
Team was early and did a great job
Bill - Kimberling City, MO
Very knowledgeable young man and extremely polite. Difficult to find those kind of people these days.
Logan does a great job and is very personable!
Joe - Kimberling City, MO
Rick - Kimberling City, MO
Great company and great people!!
Doing a tune up on a 1999 Lennox 3.5 ton heat pump system
Replaced air grill and fixed bolts in fan motor on lennox heat pump
Heat pump nothing coming on short in low voltage control wire
Cleaning a plugged up evaporator coil caused from home renovation.
Complaint of auxiliary heat running without heat pump on main system and upstairs system froze up on inside of cabniet. Diagnosis- Found A coil dirty on main floor system and also found bearings bad for upstairs system condenser fan motor. Solutions- Cleaned Indoor coil for main system and checked charge and defrost operation, also changed outdoor fan motor for upstairs system and got customer signed up for seasonal maintenance. Both systems now look good at this time.
Planned maintenance agreement heating tune up. Checked the system out and found it to be operating properly.
Installing a Lennox heat pump system. Removing old equipment and installing a 16 SEER system.
Planned maintenance agreement heating tune up. Found that the system was operating properly.
Came out for planned maintenance agreement heating tune up. On a rheem heatpump and a through the wall unit. Found that both systems were operating properly.
Bid on system replacement of old heat pump.
Doing tune up/ hvac inspection and changing out customer installed thermostat due to incorrect operation of equipment.
Out to install two bypass humidifiers got them installed and operating properly
Complaint of low air flow on certain bedrooms
Performing a heating tune up on a Ruud heat pump system. Changing filter, cleaning coils, checking system charge, checking and testing strip heat, inspecting all wiring, testing electrical components, cleaning condensation trap, and testing overall system performance.
Planned maintenance agreement heating tune up. Found one system operating properly. Found the other not defrosting. Due to bad defrost board. Replaced board
Unit making noise and fan not running. Found unit going into defrost.
Performing a heating checkout on two GeoComfort geothermal systems. Washing filters, testing and inspecting emergency heat, testing system heating, water temperatures and pressures in and out, and overall system performance.
Out for planned maintenance agreement heating tune up. Found problem with in floor heating. Found that the main circulation pump was not coming on. Order pump to replace.
Came out to investigate noises on outdoor lennox unit. Found some loose screws which I tighten to fix that problem. Found some settings that needed to be adjusted to get better performance out of the equipment. Adjusted them to optimize performance
Came out to check and see why customer was feeling cool Air and look for a cause of higher electric bills. Found that the thermostat was not operating properly and wasn't showing proper room temp. Replace thermostat to get system operating properly.
Arrived to find system not heating. Found a fault in the thermostat. Replaced thermostat. Performed safety testing. Unit is now heating properly at this time.
Doing a tune up on a Lennox heat pump system that is building up with ice.
Checking out a Lennox xp20 heat pump that is running electric strip heat only.
Complaint of low voltage fuse blown on air handler. Diagnosis- Found low voltage short on low pressure switch on heat pump. Solution- insulated wires and suction line and tested system. Showing normal operation at this time.
Performing a heating tune up on a Lennox heat pump system. Replacing MERV 10 filter, cleaning coils, checking system charge, testing electrical and strip heat, and checking overall system performance.